// CODE SNIPPET
E 503.2 Water Riser Pipe
JUMP TO FULL CODE CHAPTER
Each potable water connection shall consist of a water riser pipe that is equipped with a threaded male spigot located not less than 12 inches (305 mm) but not more than 24 inches (610 mm) above grade level for the attachment of a standard water hose. The water riser pipe shall be protected from physical damage in accordance with this code. This connection shall be equipped with a listed antisiphon backflow prevention device.
Related Code Sections
E 503.2 Manufactured/Mobile Home Parks and Recreational Vehicle Parks, Water Riser Pipe
Each potable water connection shall consist of a water riser pipe that is equipped with a threaded male spigot located not less than 12 inches (305 ...
2018 Uniform Plumbing Code of Nevada > E Manufactured/Mobile Home Parks and Recreational Vehicle Parks > E 503.0 Recreational Vehicle Park Water Connections for Individual Recreational Vehicles > E 503.2 Water Riser Pipe
1502.3.3 Alternate Water Sources for Nonpotable Applications, Discovery of Cross-Connection
: The alternate water source piping to the building shall be shutdown at the meter, and the alternate water source riser shall be drained. Potable ...
2018 Uniform Plumbing Code of Nevada > 15 Alternate Water Sources for Nonpotable Applications > 1502.0 Inspection and Testing > 1502.3 Annual Cross-Connection Inspection and Testing > 1502.3.3 Discovery of Cross-Connection
18.104.22.168.3 Installation Requirements,
Where aboveground water-filled supply pipes, risers, system risers, or feed mains pass through open areas, cold rooms, passageways, or other areas ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 8 Installation Requirements > 8.16 Piping Installation > 8.16.4 Protection of Piping > 22.214.171.124 Protection of Piping Against Freezing > 126.96.36.199.3
1605.3.3 Nonpotable Rainwater Catchment Systems, Discovery of Cross-Connection
immediately: Rainwater catchment water piping to the building shall be shutdown at the meter, and the rainwater water riser shall be drained ...
2018 Uniform Plumbing Code of Nevada > 16 Nonpotable Rainwater Catchment Systems > 1605.0 Inspection and Testing > 1605.3 Annual Cross-Connection Inspection and Testing > 1605.3.3 Discovery of Cross-Connection
P2903.3.1 Water Supply and Distribution, Maximum Pressure
valve conforming to ASSE 1003 or CSA B356 shall be installed on the domestic water branch main or riser at the connection to the water-service pipe ...
Residential Code 2012 of Nevada > 29 Water Supply and Distribution > P2903 Water-Supply System > P2903.3 Minimum Pressure > P2903.3.1 Maximum Pressure