// CODE SNIPPET
1402.8.5 Water Heaters and Hot Water Storage Tanks
JUMP TO FULL CODE CHAPTER
Hot water storage tanks shall be insulated and such insulation shall have an R-value of not less than R-12.5.
Storage tanks and heating equipment installed in outdoor locations shall be designed for outdoor installation.
Storage tank sensors shall comply with ICC 900/SRCC 300.
Related Code Sections
1402.8.5 Solar Thermal Systems, Water Heaters and Hot Water Storage Tanks
Auxiliary water heaters, boilers and water storage tanks associated with solar thermal systems shall comply with Chapter 10 and ICC 900/SRCC 300 ...
Mechanical Code 2018 of Maryland > 14 Solar Thermal Systems > 1402 Design and Installation > 1402.8 Equipment > 1402.8.5 Water Heaters and Hot Water Storage Tanks
Chapter 5 Water Heaters
valves specified in this chapter. This chapter also covers the access requirements to water heaters and hot water storage tanks to allow ...
C404.3 [CE] Commercial Energy Efficiency, Heat Traps for Hot Water Storage Tanks
Storage tank-type water heaters and hot water storage tanks that have vertical water pipes connecting to the inlet and outlet of the tank shall ...
Energy Conservation Code 2018 of Maryland > 4 [CE] Commercial Energy Efficiency > C404 Service Water Heating (Mandatory) > C404.3 Heat Traps for Hot Water Storage Tanks