// CODE SNIPPET
Section P3109 Waste ST Ack Vent
JUMP TO FULL CODE CHAPTER
The waste stack shall be vertical, and both horizontal and vertical offsets shall be prohibited between the lowest fixture drain connection and the highest fixture drain connection to the stack. Every fixture drain shall connect separately to the waste stack. The stack shall not receive the discharge of water closets or urinals.
A stack vent shall be installed for the waste stack. The size of the stack vent shall be not less than the size of the waste stack. Offsets shall be permitted in the stack vent and shall be located not less than 6 inches (152 mm) above the flood level of the highest fixture, and shall be in accordance with Section P3104.5. The stack vent shall be permitted to connect with other stack vents and vent stacks in accordance with Section P3113.3.
The waste stack shall be sized based on the total discharge to the stack and the discharge within a branch interval in accordance with Table P3109.4. The waste stack shall be the same size throughout the length of the waste stack.
For SI: 1 inch = 25.4 mm.
|MAXIMUM NUMBER OF FIXTURE UNITS (d.f.u.)|
|Total discharge into one branch interval||Total discharge for stack|
Related Code Sections
Section P3109 Vents, Waste ST Ack Vent
A waste stack shall be considered a vent for all of the fixtures discharging to the stack where installed in accordance with the requirements ...
913.4 Vents, Waste Stack Size
913.4. The waste stack shall be the same size throughout its length. TABLE 913.4 WASTE STACK VENT SIZE STACK ...
913.3 Vents, Stack Vent
A stack vent shall be provided for the waste stack . The size of the stack vent shall be not less than the size of the waste stack . Offsets ...
Section 803 Indirect/Special Waste, Special Wastes
Chemical drainage and vent systems shall be completely separated from the sanitary systems. Chemical waste shall not discharge to a sanitary drainage system ...
424.1.2 Fixtures, Faucets and Fixture Fittings, Waste Fittings
Waste fittings shall conform to ASME A112.18.2/CSA B125.2, ASTM F409 or to one of the standards listed in Tables 702.1 and 702.4 for aboveground ...
2015 Michigan Plumbing Code > 4 Fixtures, Faucets and Fixture Fittings > 424 Faucets and Other Fixture Fittings > 424.1 Approval > 424.1.2 Waste Fittings