// CODE SNIPPET
407.2.1 Waiting and Similar Areas
JUMP TO FULL CODE CHAPTER
- The spaces are not occupied as care recipient's sleeping rooms, treatment rooms, incidental uses in accordance with Section 509, or hazardous uses.
- The open space is protected by an automatic fire detection system installed in accordance with Section 907.
- The corridors onto which the spaces open, in the same smoke compartment, are protected by an automatic fire detection system installed in accordance with Section 907, or the smoke compartment in which the spaces are located is equipped throughout with quick-response sprinklers in accordance with Section 903.3.2.
- The space is arranged so as not to obstruct access to the required exits.
Related Code Sections
407.2.1 Special Detailed Requirements Based on Occupancy and Use, Waiting and Similar Areas
Waiting areas, public-use areas or group meeting spaces constructed as required for corridors shall be permitted to be open to a corridor , only ...
Building Code 2018 of Illinois > 4 Special Detailed Requirements Based on Occupancy and Use > 407 Group I-2 > 407.2 Corridors Continuity and Separation > 407.2.1 Waiting and Similar Areas
1109.12.5 Accessibility, Queue and Waiting Lines
Queue and waiting lines servicing accessible counters or check-out aisles shall be accessible ...
Building Code 2018 of Illinois > 11 Accessibility > 1109 Other Features and Facilities > 1109.12 Service Facilities > 1109.12.5 Queue and Waiting Lines
227.5 Scoping Requirements, Queues and Waiting Lines
Queues and waiting lines servicing counters or check-out aisles required to comply with 904.3 or 904.4 shall comply with 403 ...
2018 Illinois Accessibility Code > 2 Scoping Requirements > 227 Sales and Service > 227.5 Queues and Waiting Lines
1029.4 Means of Egress, Foyers and Lobbies
In Group A-1 occupancies, where persons are admitted to the building at times when seats are not available, such persons shall be allowed to wait ...