// CODE SNIPPET
(E) Voltage Marking
Related Code Sections
(E) Wiring and Protection, Voltage Marking
Circuit breakers shall be marked with a voltage rating not less than the nominal system voltage that is indicative of their capability to interrupt ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 240 Overcurrent Protection > 240.83 Marking > (E) Voltage Marking
(J) Special Conditions, Marking
Cables shall be marked in accordance with 310.8(A)(2), (A)(3), (A)(4), (A)(5), and Table 725.179(J). Voltage ratings shall not be marked ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 725 Class 1, Class 2, and Class 3 Remote- Control, Signaling, and Power-Limited Circuits > 725.179 Listing and Marking of Class 2, Class 3, and Type PLTC Cables > (J) Marking
820.179 Communications Systems, Coaxial Cables
Cables shall be listed in accordance with 820.179(A) and marked in accordance with Table 820.179 and 820.179(B). The cable voltage rating shall ...
National Electrical Code 2020 of Minnesota > 8 Communications Systems > 820 Community Antenna Television and Radio Distribution Systems > 820.179 Coaxial Cables
336.120 Wiring Methods and Materials, Marking
There shall be no voltage marking on a Type TC cable employing thermocouple extension wire ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 336 Power and Control Tray Cable: Type TC > 336.120 Marking
(I) Special Conditions, Cable Marking
The cable shall be marked in accordance with Table 760.179(I). The voltage rating shall not be marked on the cable. Cables that are listed ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 760 Fire Alarm Systems > 760.179 Listing and Marking of PLFA Cables and Insulated Continuous Line-Type Fire Detectors > (I) Cable Marking