// CODE SNIPPET
Section P-601 Vertical Piping
JUMP TO FULL CODE CHAPTER
Vertical piping shall be secured at sufficient intervals to keep the pipe in alignment and to carry the weight of the pipe and contents.
Supports shall provide secure support for the pipe without excessive strain on joints or connections and shall properly transmit the load to the building structure or to independent posts, piers, and foundations.
All vertical drainage piping shall have base supports and, when more than 30 feet in height, shall have intermediate supports spaced not more than 2 stories or 25 feet on centers. Closet bends, traps, trap-arms and similar branches shall be firmly secured against movement in any direction.
Exception: No-hub cast iron soil pipe shall be supported with a riser clamp located at each floor. When the distance between floors is greater than 10 feet, the vertical piping shall be supported every 10 feet using riser clamps where possible or rigid supports securely fastened to the building structure.
Aluminum and plastic pipe shall be supported a minimum of at least 5 feet on centers and closer, if required, to prevent horizontal deformation of the piping.
Related Code Sections
Section P-601 Pipe Supports, Vertical Piping
Vertical piping shall be secured at sufficient intervals to keep the pipe in alignment and to carry the weight of the pipe and contents ...
917.4.3 Vents, Vertical Piping in Branch
The length of vertical piping in a fixture drain connecting to a horizontal branch shall not be considered in computing the fixture's distance ...
Plumbing Code 2018 of Philadelphia > 9 Vents > 917 Single-Stack Vent System > 917.4 Length of Horizontal Branches > 917.4.3 Vertical Piping in Branch
917.5 Vents, Minimum Vertical Piping Size From Fixture
The vertical portion of piping in a fixture drain to a horizontal branch shall be 2 inches (51 mm). The minimum size of the vertical portion ...
Plumbing Code 2018 of Philadelphia > 9 Vents > 917 Single-Stack Vent System > 917.5 Minimum Vertical Piping Size From Fixture
3.5.9 Definitions, Riser Nipple
A vertical pipe between the cross main and branch line ...
Standard for the Installation of Sprinkler Systems 2016 of Philadelphia > 3 Definitions > 3.5* System Component Definitions > 3.5.9 Riser Nipple
3.5.13 Definitions, System Riser
The aboveground horizontal or vertical pipe between the water supply and the mains (cross or feed) that contains a control valve (either directly ...
Standard for the Installation of Sprinkler Systems 2016 of Philadelphia > 3 Definitions > 3.5* System Component Definitions > 3.5.13 System Riser