// CODE SNIPPET
188.8.131.52 Ventilation Rate
Related Code Sections
1105.6.3 Refrigeration, Ventilation Rate
operating and emergency conditions, as required by Sections 1184.108.40.206 and 1220.127.116.11. The minimum required ventilation rate for ammonia shall be 30 air ...
Mechanical Code 2015 of West Virginia > 11 Refrigeration > 1105 Machinery Room, General Requirements > 1105.6 Ventilation > 1105.6.3 Ventilation Rate
18.104.22.168 Compressed Gases and Cryogenic Fluids, Ventilation Rate
Mechanical exhaust or fixed natural ventilation shall be provided at a rate of not less than 1 scf/min/ft 2 (0.3048 Nm 3 /min/m 2 ) of floor area ...
Fire Code 2018 of West Virginia > 63 Compressed Gases and Cryogenic Fluids > 63.2 Building-Related Controls > 63.2.16 Ventilation > 22.214.171.124 Ventilation Rate
502.4.2 Exhaust Systems, Ventilation Rate in Rooms
Continuous ventilation shall be provided at a rate of not less than 1 cubic foot per minute per square foot (cfm/ft 2 ) [0.00508 m 3 /(s • m 2 ...
Mechanical Code 2015 of West Virginia > 5 Exhaust Systems > 502 Required Systems > 502.4 Stationary Storage Battery Systems > 502.4.2 Ventilation Rate in Rooms
M1507.3.3 Exhaust Systems, Mechanical Ventilation Rate
The whole-house mechanical ventilation system shall provide outdoor air at a continuous rate of not less than that determined in accordance ...
Residential Code 2015 of West Virginia > 15 Exhaust Systems > M1507 Mechanical Ventilation > M1507.3 Whole-House Mechanical Ventilation System > M1507.3.3 Mechanical Ventilation Rate
1106.3 Refrigeration, Ammonia Room Ventilation
Ventilation systems in ammonia machinery rooms shall be operated continuously at the ventilation rate specified in Section 1105.6.3. Exceptions ...
Mechanical Code 2015 of West Virginia > 11 Refrigeration > 1106 Machinery Room, Special Requirements > 1106.3 Ammonia Room Ventilation