// CODE SNIPPET
§27-405 Ventilation of Storage Occupancies
JUMP TO FULL CODE CHAPTER
Rooms or spaces used for the storage of flammable paints, solvents, anesthetic agents, fuel or other oils having a flashpoint under two hundred degrees Fahrenheit (Tag closed cup) or other inflammable vaporous materials shall be vented to the outdoors by gravity or mechanical means, with independent supply and exhaust openings or ducts. If ventilation is provided by gravity means, the total net free openable area of supply and exhaust openings shall be equal to at least one percent of the floor area of the room, equally divided between supply and exhaust. If ventilation is provided by mechanical means, the system shall be designed to provide at least two air changes per hour. Where there are explosion hazards, see section 27-401 of this article. The construction of all ventilating systems shall be in accordance with the requirements of subchapter thirteen of this chapter.
Related Code Sections
§27-405 Special Uses and Occupancies, Ventilation of Storage Occupancies
Rooms or spaces used for the storage of flammable paints, solvents, anesthetic agents, fuel or other oils having a flashpoint under two hundred ...
NYC 1968 Code (Vol I) > 7 Special Uses and Occupancies > 2 High Hazard Occupancies > §27-405 Ventilation of Storage Occupancies
§27-521 Special Uses and Occupancies, Ventilation
Mechanical ventilation systems for storage vaults shall be adequate to effect ten complete air changes per hr. Exhaust shall be taken from within ...
NYC 1968 Code (Vol I) > 7 Special Uses and Occupancies > 20 Occupancies Involving Storage of Nitric Acid > §27-521 Ventilation
§28-118.11 Administration, Certificates of Compliance
conditioning and ventilation systems. Elevators, escalators, moving walkways and dumbwaiters. Fuel burning and fuel oil storage equipment. Refrigeration ...
NYC General Admin. Provisions 2014 > 1 Administration > 118 Certificates of Occupancy > §28-118.11 Certificates of Compliance
Article 6 Ventilation [PDF] (page 5)
and the Commissioner of Health may be used for such ventilation. c. Auditoriums, assembly rooms, and other rooms where there are more than 75 occupants ...
414.3 Special Detailed Requirements Based on Use and Occupancy, Ventilation
are or may be emitted due to the processing, use, handling or storage of materials shall be mechanically ventilated as required by the New York City Fire ...
NYC Building Code 2008 > 4 Special Detailed Requirements Based on Use and Occupancy > 414 Hazardous Materials > 414.3 Ventilation