// CODE SNIPPET
§27-764 Ventilation of Boiler Rooms
JUMP TO FULL CODE CHAPTER
Boiler rooms shall be ventilated in a manner that will provide air for combustion in accordance with the provisions of subchapter fourteen of this chapter and also prevent the accumulation of hot air over or near the equipment within the room.
Related Code Sections
§27-764 Light, Heat, Ventilation and Noise Control, Ventilation of Boiler Rooms
Boiler rooms shall be ventilated in a manner that will provide air for combustion in accordance with the provisions of subchapter fourteen ...
NYC 1968 Code (Vol I) > 12 Light, Heat, Ventilation and Noise Control > 8 Ventilation of Special Spaces > §27-764 Ventilation of Boiler Rooms
§27-424 Special Uses and Occupancies, Ventilation
Boiler and furnace rooms shall be ventilated in accordance with the provisions of section 27-807 of article nine of subchapter fourteen ...
NYC 1968 Code (Vol I) > 7 Special Uses and Occupancies > 5 Boiler and Furnace Rooms > §27-424 Ventilation
304.4.2 General Regulations, Ventilation Air for Fuel Burning Devices
a negative or positive pressure in the boiler room and to discharge the ventilation directly to the outside ...
NYC Fuel Gas Code 2014 > 3 General Regulations > 304 Combustion, Ventilation and Dilution Air > 304.4 Circulation of Air > 304.4.2 Ventilation Air for Fuel Burning Devices
Article 6 Ventilation [PDF] (page 11)
resistive rating where they are located within the boiler room. 28. OPENINGS IN VENTILATING SHAFTS. Where a duct serves two or more floors, approved fire ...
926.2.1 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Boiler Rooms
All boilers supported on floors above a story having dwelling units shall be supported on resilient isolators having a minimum static deflection of 1 ...
NYC Mechanical Code 2008 > 9 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment > 926 Noise Control Requirements > 926.2 Minimum Structure-Borne Noise and Vibration Isolation Requirements > 926.2.1 Boiler Rooms