// CODE SNIPPET
[F] 502.9.8.1 Ventilated Areas
Related Code Sections
502.9.8.1 Exhaust Systems, Ventilated Areas
The room or area in which indoor gas cabinets or exhausted enclosures are located shall be provided with exhaust ventilation. Gas cabinets ...
2015 Michigan Mechanical Code > 5 Exhaust Systems > 502 Required Systems > 502.9 Hazardous Materials-Requirements for Specific Materials > 502.9.8 Highly Toxic and Toxic Compressed Gases - Quantities Exceeding the Maximum Allowable Quantity Per Control Area > 502.9.8.1 Ventilated Areas
402.2 Ventilation, Ventilation Area Required
The minimum openable area to the outdoors shall be 4 percent of the floor area being ventilated ...
2015 Michigan Mechanical Code > 4 Ventilation > 402 Natural Ventilation > 402.2 Ventilation Area Required
1203.5.1 Interior Environment, Ventilation Area Required
The openable area of the openings to the outdoors shall be not less than 4 percent of the floor area being ventilated ...
2015 Michigan Building Code > 12 Interior Environment > 1203 Ventilation > 1203.5 Natural Ventilation > 1203.5.1 Ventilation Area Required
R806.2 Roof-Ceiling Construction, Minimum Vent Area
The minimum net free ventilating area shall be 1 / 150 of the area of the vented space. Exception ...
2015 Michigan Residential Code > 8 Roof-Ceiling Construction > R806 Roof Ventilation > R806.2 Minimum Vent Area