// CODE SNIPPET
5.508.2.2.2.1 Valve Caps
JUMP TO FULL CODE CHAPTER
For systems with a refrigerant charge of 5 pounds or more, valve caps shall be brass or steel and not plastic.
Related Code Sections
5.508.2.2.2.1 Nonresidential Mandatory Measures, Valve Caps
For systems with a refrigerant charge of 5 pounds or more, valve caps shall be brass or steel and not plastic ...
Los Angeles Green Building Code > 5 Nonresidential Mandatory Measures > 5.508 Outdoor Air Quality > 5.508.2 Supermarket Refrigerant Leak Reduction > 5.508.2.2 Valves > 5.508.2.2.2 Access Valves > 5.508.2.2.2.1 Valve Caps
5003.10.1 Hazardous Materials—General Provisions, Valve Protection
of highly toxic or toxic compressed gases shall have their valve outlets capped or plugged with an approved closure device in accordance with Chapter 53 ...
Los Angeles Fire Code > 50 Hazardous Materials—General Provisions > 5003 General Requirements > 5003.10 Handling and Transportation > 5003.10.1 Valve Protection
5303.6.2 Compressed Gases, Caps and Plugs
Compressed gas containers, cylinders and tanks designed for valve protection caps or other protective devices shall have the caps or devices in place ...
Los Angeles Fire Code > 53 Compressed Gases > 5303 General Requirements > 5303.6 Valve Protection > 5303.6.2 Caps and Plugs
3134B.3.1 [DPH] Public Pools, Compressed Gas Containers
Each container or cylinder shall be secured to prevent accidental movement. A valve protection cap shall be provided to cover the discharge valve ...
Los Angeles Building Code > 31B [DPH] Public Pools > 3134B Disinfectant Feeders > 3134B.3 Compressed Chlorine Gas Disinfectant Equipment > 3134B.3.1 Compressed Gas Containers