// CODE SNIPPET
(2) Utilization Equipment Fastened in Place
Related Code Sections
(2) Wiring and Protection, Utilization Equipment Fastened in Place
The total rating of utilization equipment fastened in place, other than luminaires, shall not exceed 50 percent of the branch-circuit ampere rating ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 210 Branch Circuits > 210.23 Permissible Loads, Multiple-Outlet Branch Circuits > (A) 15- And 20-Ampere Branch Circuits > (2) Utilization Equipment Fastened in Place
(A) Wiring and Protection, Motor-Operated and Combination Loads
equipment, or both, Article 440 shall apply. For circuits supplying loads consisting of motor-operated utilization equipment that is fastened in place ...
National Electrical Code 2020 of Minnesota > 2 Wiring and Protection > 220 Branch-Circuit, Feeder, and Service Load Calculations > 220.18 Maximum Loads > (A) Motor-Operated and Combination Loads