// CODE SNIPPET
1220.1 Use of Chemical Additives and Corrosive Fluids
JUMP TO FULL CODE CHAPTER
Where auxiliary systems contain chemical additives, corrosive fluids, or both not intended or designed for use in the primary system, a double wall heat exchanger shall be used in accordance with Section 1218.1. The chemical additives in the auxiliary systems shall be compatible with auxiliary system components and accepted for use by the heat exchanger manufacturer.
Related Code Sections
1220.1 Hydronics, Use of Chemical Additives and Corrosive Fluids
Where auxiliary systems contain chemical additives, corrosive fluids, or both not intended or designed for use in the primary system, a double wall ...
2018 Uniform Mechanical Code of Nevada > 12 Hydronics > 1220.0 Auxiliary Systems > 1220.1 Use of Chemical Additives and Corrosive Fluids
1202.0 Hydronics, Protection of Potable Water Supply
system. Piping, components and devices in contact with the potable water shall be approved for such use and where an additive is used it shall ...
603.5.14.2 Water Supply and Distribution, Chemicals
Where antifreeze, corrosion inhibitors, or other chemicals are added to a fire protection system supplied from a potable water supply, the potable ...
2018 Uniform Plumbing Code of Nevada > 6 Water Supply and Distribution > 603.0 Cross-Connection Control > 603.5 Specific Requirements > 603.5.14 Protection From Fire Systems > 603.5.14.2 Chemicals
22.214.171.124* Systems Acceptance,
Additives, corrosive chemicals such as sodium silicate, or derivatives of sodium silicate, brine, or similar acting chemicals shall not be used while ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 25 Systems Acceptance > 25.2 Acceptance Requirements > 25.2.1* Hydrostatic Tests > 126.96.36.199*
(B) Wiring Methods and Materials, Corrosive Influences
RTRC shall be permitted in locations subject to severe corrosive influences as covered in 300.6 and where subject to chemicals for which ...
National Electrical Code 2017 of Nevada > 3 Wiring Methods and Materials > 355 Reinforced Thermosetting Resin Conduit: Type RTRC > 355.10 Uses Permitted > (B) Corrosive Influences