Go To Full Code Chapter
605.2 Height and Depth
Urinals shall be the stall-type or the wall-hung type with the rim 17 inches (430 mm) maximum above the finish floor or ground. Urinals shall be 13 1/2 inches (345 mm) deep minimum measured from the outer face of the urinal rim to the back of the fixture.
605.3 Clear Floor Space
605.4 Flush Controls
Related Code Sections
213.3.3 Scoping Requirements, Urinals
Where more than one urinal is provided, at least one shall comply with 605 ...
605 Plumbing Elements and Facilities, Urinals
Urinals shall comply with 605. Advisory 605.1 General. Stall-type urinals provide greater accessibility for a broader range of persons ...
213.3 Scoping Requirements, Plumbing Fixtures and Accessories
where six or more toilet compartments are provided, or where the combination of urinals and water closets totals six or more fixtures. Advisory ...
213.3.1 Scoping Requirements, Toilet Compartments
of urinals and water closets totals six or more fixtures. Advisory 213.3.1 Toilet Compartments. A toilet compartment is a partitioned space ...
213 Scoping Requirements, Toilet Facilities and Bathing Facilities
Unisex toilet rooms shall contain not more than one lavatory, and two water closets without urinals or one water closet and one urinal. Unisex ...