// CODE SNIPPET
3304.10.5 Unused High Explosives
JUMP TO FULL CODE CHAPTER
High explosives in storage at a job site at the completion of blasting operations, or which are not otherwise to be used at the job site, shall be removed from the job site and transported to a vendor's facility. The vendor may store and supply for use unopened cases of high explosives. The vendor may not supply open cases of high explosives for use unless the explosives are packaged in an approved manner, and their condition certified in writing in an approved manner by the magazine keeper previously responsible for their storage.
Related Code Sections
G.3.1 High Pressure Natural Gas Installations, Explosion Venting
Appliances and equipment using gas at or above 125 psig (862 kPa gauge) shall be located in rooms provided with explosion venting in accordance ...
NYC Fuel Gas Code 2014 > G High Pressure Natural Gas Installations > G.3 High Hazard > G.3.1 Explosion Venting
711.3.3 Fire-Resistance-Rated Construction, Unusable Space
In 1-hour fire-resistance-rated floor construction, the ceiling membrane is not required to be installed over unusable crawl spaces not intended ...
NYC Building Code 2008 > 7 Fire-Resistance-Rated Construction > 711 Horizontal Assemblies > 711.3 Fire-Resistance Rating > 711.3.3 Unusable Space
712.3.3 Fire and Smoke Protection Features, Unusable Space
In 1-hour fire-resistance-rated floor assemblies, the ceiling membrane is not required to be installed over unusable crawl spaces not intended ...
NYC Building Code 2014 > 7 Fire and Smoke Protection Features > 712 Horizontal Assemblies > 712.3 Fire-Resistance Rating > 712.3.3 Unusable Space
G.2.5.1 High Pressure Natural Gas Installations, Explosion Prevention
), explosion prevention systems shall be provided in accordance with NFPA 69 ...
NYC Fuel Gas Code 2014 > G High Pressure Natural Gas Installations > G.2 Construction Requirements > G.2.5 Ventilation > G.2.5.1 Explosion Prevention
1625.6 Structural Design, Gas Explosions
mm) of such piping shall be designed to resist a potential gas explosion. The structure shall be designed to account for the potential loss ...
NYC Building Code 2008 > 16 Structural Design > 1625 Structural Integrity — Prescriptive Requirements > 1625.6 Gas Explosions