// CODE SNIPPET
Section P-805 Underground Water Pipe
JUMP TO FULL CODE CHAPTER
When underground water service piping or water distribution piping and sewer or drain piping are laid in the same trench, the water service pipe or the water distribution pipe shall be laid on a bench or solidly tamped backfill at a level at least 12 inches above the top of the drainage pipe and at least 12 inches horizontally from the center line of the drainage pipe, and shall conform to Sections P-809 and P-904.4.
Related Code Sections
Section P-805 Water Supply and Distribution, Underground Water Pipe
When underground water service piping or water distribution piping and sewer or drain piping are laid in the same trench, the water service pipe ...
E3608.1.1 Services, Metal Underground Water Pipe
A metal underground water pipe that is in direct contact with the earth for 10 feet (3048 mm) or more, including any well casing effectively bonded ...
2018 Philadelphia Residential Code > 36 Services > E3608 Grounding Electrode System > E3608.1 Grounding Electrode System > E3608.1.1 Metal Underground Water Pipe
P-809.4 Water Supply and Distribution, Below Ground
Water distribution piping and water piping underground shall be of brass, type "L" copper or heavier, cast iron, or plastic cold water pipe. Temp ...
Philadelphia Plumbing Code > 8 Water Supply and Distribution > P-809 Material for Water Pipe, Tubing and Fittings > P-809.4 Below Ground
P-1005.6 Storm Water Drainage Piping, Clearance From Buildings
All underground storm water piping installed parallel to a foundation wall shall be at least 3 feet from the building foundation wall when the depth ...
Philadelphia Plumbing Code > 10 Storm Water Drainage Piping > P-1005 Materials > P-1005.6 Clearance From Buildings
Section P-1005 Storm Water Drainage Piping, Materials
All underground storm water piping installed parallel to a foundation wall shall be at least 3 feet from ...