// CODE SNIPPET
(A) Type of Feeder
JUMP TO FULL CODE CHAPTER
Multiple feeders of unlimited quantity shall be permitted, provided that all multiple feeders are part of a single system. Where combined, neutral conductors in a given raceway shall be of sufficient ampacity to carry the maximum unbalanced current supplied by multiple feeder conductors in the same raceway, but they need not be greater than the ampacity of the neutral conductor supplying the primary stage switchboard. Parallel neutral conductors shall comply with 310.10(G).
Installations with separate feeders to a single primary stage switchboard shall have a disconnecting means for each feeder. The primary stage switchboard shall have a permanent and obvious label stating the number and location of disconnecting means. If the disconnecting means are located in more than one distribution switchboard, the primary stage switchboard shall be provided with barriers to correspond with these multiple locations.
Related Code Sections
(A) Special Occupancies, Type of Feeder
Feeders supplying stage switchboards shall be one of the types in 520.27(A)(1) through (A)(3 ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 520 Theaters, Audience Areas of Motion Picture and Television Studios, Performance Areas, and Similar Locations > 520.27 Stage Switchboard Feeders > (A) Type of Feeder
(A) Equipment for General Use, Specific Load
motor supplied by the feeder [based on the maximum permitted value for the specific type of a protective device in accordance with 430.52, or 440.22(A ...
National Electrical Code 2020 of Minnesota > 4 Equipment for General Use > 430 Motors, Motor Circuits, and Controllers > 430.62 Rating or Setting — Motor Load > (A) Specific Load
(E) Special Occupancies, Equipment Grounding and Bonding
Where a grounded electrical distribution system is used and metal feeder raceway or Type MC or MI cable that qualifies as an equipment grounding ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.19 Category 1 (Critical Care) Spaces > (E) Equipment Grounding and Bonding
340.1 Wiring Methods and Materials, Scope
This article covers the use, installation, and construction specifications for underground feeder and branch-circuit cable, Type UF ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 340 Underground Feeder and Branch-Circuit Cable: Type UF > 340.1 Scope
(B) Wiring Methods and Materials, Branch Circuits or Feeders
Type USE cable installed as underground feeder and branch circuit cable shall comply with Part II of Article 340. Exception: Single-conductor Type ...
National Electrical Code 2020 of Minnesota > 3 Wiring Methods and Materials > 338 Service-Entrance Cable: Types SE and USE > 338.10 Uses Permitted > (B) Branch Circuits or Feeders