// CODE SNIPPET
1014.3.2 Type II
JUMP TO FULL CODE CHAPTER
Handrails with a perimeter greater than 61/4 inches (160 mm) shall provide a graspable finger recess area on both sides of the profile. The finger recess shall begin within a distance of 3/4 inch (19 mm) measured vertically from the tallest portion of the profile and achieve a depth of not less than 5/16 inch (8 mm) within 7/8 inch (22 mm) below the widest portion of the profile. This required depth shall continue for not less than 3/8 inch (10 mm) to a level that is not less than 13/4 inches (45 mm) below the tallest portion of the profile. The width of the handrail above the recess shall be not less than 11/4 inches (32 mm) to not greater than 23/4 inches (70 mm). Edges shall have a minimum radius of 0.01 inch (0.25 mm).
Related Code Sections
1014.3.2 Means of Egress, Type II
Handrails with a perimeter greater than 6 1 / 4 inches (160 mm) shall provide a graspable finger recess area on both sides of the profile. The ...
Building Code 2018 of Illinois > 10 Means of Egress > 1014 Handrails > 1014.3 Handrail Graspability > 1014.3.2 Type II
507.6 General Building Heights and Areas, Group A-3 Buildings of Type II Construction
, exhibition hall, gymnasium, lecture hall, indoor swimming pool or tennis court of Type II construction, shall not be limited provided all ...
Building Code 2018 of Illinois > 5 General Building Heights and Areas > 507 Unlimited Area Buildings > 507.6 Group A-3 Buildings of Type II Construction
602.2 Types of Construction, Types I and II
Types I and II construction are those types of construction in which the building elements listed in Table 601 are of noncombustible materials ...
Building Code 2018 of Illinois > 6 Types of Construction > 602 Construction Classification > 602.2 Types I and II
705.2.1 Fire and Smoke Protection Features, Types I and II Construction
Projections from walls of Type I or II construction shall be of noncombustible materials or combustible materials as allowed by Sections 705.2.3.1 ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 705 Exterior Walls > 705.2 Projections > 705.2.1 Types I and II Construction
1405.1.1 Exterior Walls, Types I, II, III and IV Construction
On buildings of Types I, II, III and IV construction, exterior wall coverings shall be permitted to be constructed of combustible materials ...
Building Code 2018 of Illinois > 14 Exterior Walls > 1405 Combustible Materials on the Exterior Side of Exterior Walls > 1405.1 Combustible Exterior Wall Coverings > 1405.1.1 Types I, II, III and IV Construction