// CODE SNIPPET
1206.2 Type I Solvents
JUMP TO FULL CODE CHAPTER
Related Code Sections
1206.2 Dry Cleaning, Type I Solvents
The maximum quantity of Type I solvents permitted at any work station shall be 1 gallon (4 L). Class I solvents shall be stored in approved safety ...
Fire Code 2009 of Massachusetts > 12 Dry Cleaning > 1206 Spotting and Pretreating > 1206.2 Type I Solvents
1203.2 Dry Cleaning, Classification of Dry Cleaning Plants and Systems
Dry cleaning plants and systems shall be classified based on the solvents used as follows: Type I—systems using Class I solvents. Type II ...
Fire Code 2009 of Massachusetts > 12 Dry Cleaning > 1203 Classifications > 1203.2 Classification of Dry Cleaning Plants and Systems
1204.1 Dry Cleaning, Prohibited Use
Type I dry cleaning plants shall be prohibited. Limited quantities of Class I solvents stored and used in accordance with this section shall ...
Fire Code 2009 of Massachusetts > 12 Dry Cleaning > 1204 General Requirements > 1204.1 Prohibited Use
1205.1.5 Dry Cleaning, Equipment Maintenance and Housekeeping
Proper maintenance and operating practices shall be observed in order to prevent the leakage of solvent or the accumulation of lint. The handling ...
Fire Code 2009 of Massachusetts > 12 Dry Cleaning > 1205 Operating Requirements > 1205.1 General > 1205.1.5 Equipment Maintenance and Housekeeping
3405.3.6.2.1 Flammable and Combustible Liquids, Solvents
Solvents shall be classified and shall be compatible with the machines within which they are used ...
Fire Code 2009 of Massachusetts > 34 Flammable and Combustible Liquids > 3405 Dispensing, Use, Mixing and Handling > 3405.3 Use, Dispensing and Mixing Inside of Buildings > 3405.3.6 Cleaning With Flammable and Combustible Liquids > 3405.3.6.2 Listed and Approved Machines > 3405.3.6.2.1 Solvents