// CODE SNIPPET
(A) Two Independent Power Sources
Related Code Sections
(A) Special Occupancies, Two Independent Power Sources
Essential electrical systems shall have a minimum of the following two independent sources of power: a normal source generally supplying the entire ...
National Electrical Code 2020 of Minnesota > 5 Special Occupancies > 517 Health Care Facilities > 517.30 Sources of Power > (A) Two Independent Power Sources
29.6.2 Single- And Multiple-Station Alarms and Household Fire Alarm Systems, Household Fire Alarm Systems
Power for household fire alarm systems shall comply with the following requirements: Household fire alarm systems shall have two independent power ...
National Fire Alarm and Signaling Code 2016 of Minnesota > 29 Single- And Multiple-Station Alarms and Household Fire Alarm Systems > 29.6 Power Supplies > 29.6.2 Household Fire Alarm Systems
700.17 Special Conditions, Branch Circuits for Emergency Lighting
or more branch circuits supplied from separate and complete systems with independent power sources. One of the two power sources and systems shall be part ...
National Electrical Code 2020 of Minnesota > 7 Special Conditions > 700 Emergency Systems > 700.17 Branch Circuits for Emergency Lighting
513.11 Exhaust Systems, Power Systems
The smoke control system shall be supplied with two sources of power. Primary power shall be the normal building power systems. Secondary power shall ...
Minnesota Mechanical Code 2015 > 5 Exhaust Systems > 513 Smoke Control Systems > 513.11 Power Systems