// CODE SNIPPET
1910.269(v)(10) Turbine Generators
JUMP TO FULL CODE CHAPTER
Smoking and other ignition sources are prohibited near hydrogen or hydrogen sealing systems, and signs warning of the danger of explosion and fire shall be posted.
A sufficient quantity of inert gas shall be available to purge the hydrogen from the largest generator.
Excessive hydrogen makeup or abnormal loss of pressure shall be considered as an emergency and shall be corrected immediately.
Related Code Sections
1910.269(v)(10) Special Industries, Turbine Generators
shall be available to purge the hydrogen from the largest generator ...
OSHA 1910 General Industry > R Special Industries > 1910.269 Electric Power Generation, Transmission, and Distribution > 1910.269(v) Power Generation > 1910.269(v)(10) Turbine Generators
1910.253(f) Welding, Cutting, and Brazing, Acetylene Generators
Generators shall be of approved construction and shall be plainly marked with the maximum rate of acetylene in cubic feet per hour for which ...
OSHA 1910 General Industry > Q Welding, Cutting, and Brazing > 1910.253 Oxygen-Fuel Gas Welding and Cutting > 1910.253(f) Acetylene Generators
1910.110(e)(11) Hazardous Materials, Stationary Engines in Buildings
Stationary engines and gas turbines installed in buildings, including portable engines used instead of or to supplement stationary engines, shall ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.110 Storage and Handling of Liquefied Petroleum Gases > 1910.110(e) Liquefied Petroleum Gas as a Motor Fuel > 1910.110(e)(11) Stationary Engines in Buildings
1910.102(c) Hazardous Materials, Generators and Filling Cylinders
Employers must ensure that facilities, equipment, structures, or installations used to generate acetylene or to charge (fill) acetylene cylinders ...
OSHA 1910 General Industry > H Hazardous Materials > 1910.102 Acetylene > 1910.102(c) Generators and Filling Cylinders
1910.211(f)(9) Machinery and Machine Guarding, Prime Movers
Prime movers include steam, gas, oil, and air engines, motors, steam and hydraulic turbines, and other equipment used as a source of power ...
OSHA 1910 General Industry > O Machinery and Machine Guarding > 1910.211 Definitions > 1910.211(f) > 1910.211(f)(9) Prime Movers