// CODE SNIPPET
704.5 Truss Protection
JUMP TO FULL CODE CHAPTER
The required thickness and construction of fire-resistance-rated assemblies enclosing trusses shall be based on the results of full-scale tests or combinations of tests on truss components or on approved calculations based on such tests that satisfactorily demonstrate that the assembly has the required fire resistance.
Related Code Sections
704.5 Fire and Smoke Protection Features, Truss Protection
The required thickness and construction of fire-resistance-rated assemblies enclosing trusses shall be based on the results of full-scale tests ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 704 Fire-Resistance Rating of Structural Members > 704.5 Truss Protection
7188.8.131.52 Fire and Smoke Protection Features, Structural Steel Trusses
The fire resistance of structural steel trusses protected with fire-resistant materials sprayed to each of the individual truss elements shall ...
Building Code 2018 of Illinois > 7 Fire and Smoke Protection Features > 722 Calculated Fire Resistance > 722.5 Steel Assemblies > 722.5.2 Structural Steel Beams and Girders > 7184.108.40.206 Structural Steel Trusses
2303.4 Wood, Trusses
Wood trusses shall comply with Sections 2303.4.1 through 2303.4.7 ...
1705.14.4.7 Special Inspections and Tests, Joists and Trusses
At joists and trusses, thickness measurements shall be made at seven locations around the joist or truss at each end of a 12-inch (305 mm) length ...
Building Code 2018 of Illinois > 17 Special Inspections and Tests > 1705 Required Special Inspections and Tests > 1705.14 Sprayed Fire-Resistant Materials > 1705.14.4 Thickness > 1705.14.4.7 Joists and Trusses
18.12 Earthquake-Resistant Structures, Diaphragms and Trusses
Section 18.12.11 shall apply to structural trusses ...
Building Code Requirements for Structural Concrete of Illinois > 18 Earthquake-Resistant Structures > 18.12 Diaphragms and Trusses