// CODE SNIPPET
P-707.2 Trough Urinals
JUMP TO FULL CODE CHAPTER
Trough urinals shall only be installed on such premises as parks or buildings of temporary occupancy. They shall be provided with backs and made in one piece of cast iron, enameled on the inside. They shall not be less than 6 inches deep. The perforated wash down pipe shall be securely clamped as high as practicable to the back of the urinal, and the perforations shall be of such size and so arranged as to discharge an even curtain of water against the back of the urinal. Trough urinals shall be either arranged for a continuous flow of flushing water with an overhead supply or shall be equipped with automatic flush tanks having a flushing capacity of not less than 1 1/2 gallons for each 2 feet of urinal length.
Related Code Sections
P-707.2 Plumbing Fixtures, Trough Urinals
Trough urinals shall only be installed on such premises as parks or buildings of temporary occupancy. They shall be provided with backs and made ...
401.2 Fixtures, Faucets and Fixture Fittings, Prohibited Fixtures and Connections
be prohibited. Trough urinals shall be prohibited ...
Plumbing Code 2018 of Philadelphia > 4 Fixtures, Faucets and Fixture Fittings > 401 General > 401.2 Prohibited Fixtures and Connections
P-506.1 Traps, Cleanouts, Interceptors, and Backwater Valves, General
, Trough 1 1 / 2 Urinal, Wall 1 1 / 2 Wash Fountain 2 Wash Sink, 6 ft. 1 1 / 2 ...
Philadelphia Plumbing Code > 5 Traps, Cleanouts, Interceptors, and Backwater Valves > P-506 Sizes of Fixture Traps and Fixture Drains > P-506.1 General
P-904.1 Soil and Waste Piping, Fixture-Unit Values
— 4 Urinal, pedestal, siphon-jet, and blow-out — 6 Urinal Trough; for each 5 feet — 2 ...
P-714.1.1 Plumbing Fixtures, Trough Drains
A trough drain shall be considered as a floor drain. The dimensions of a trough drain shall not exceed 12 inches in width and 12 feet in length ...
Philadelphia Plumbing Code > 7 Plumbing Fixtures > P-714 Floor Drains > P-714.1 Outlet > P-714.1.1 Trough Drains