// CODE SNIPPET
JUMP TO FULL CODE CHAPTER
Gray water piping discharging into the surge tank or having a direct connection to the sanitary drain or sewer piping shall be downstream of an approved water seal type trap(s). Where no such trap(s) exists, an approved vented running trap shall be installed upstream of the connection to protect the building from possible waste or sewer gases.
Related Code Sections
1004.0 Traps and Interceptors, Traps
No form of trap that depends for its seal upon the action of movable parts shall be used. No trap that has concealed interior partitions, except ...
1503.9.6 Alternate Water Sources for Nonpotable Applications, Trap
of an approved water seal type trap(s). Where no such trap(s) exists, an approved vented running trap shall be installed upstream of the connection to protect ...
2018 Uniform Plumbing Code of Nevada > 15 Alternate Water Sources for Nonpotable Applications > 1503.0 Gray Water Systems > 1503.9 Gray Water System Components > 1503.9.6 Trap
Chapter 32 Traps
User notes: About this chapter: Chapter 32 regulates the design of fixture traps, methods for preventing evaporation of trap seals in traps ...
P2911.3 Water Supply and Distribution, Traps
Traps serving fixtures and devices discharging wastewater to on-site nonpotable water reuse systems shall comply with the Section P3201.2 ...
Residential Code 2018 of Nevada > 29 Water Supply and Distribution > P2911 On-Site Nonpotable Water Reuse Systems > P2911.3 Traps