// CODE SNIPPET
P-901.1.1 Transformer Vault
JUMP TO FULL CODE CHAPTER
No piping connected to the plumbing system shall be installed in any transformer vault.
Related Code Sections
P-901.1.1 Soil and Waste Piping, Transformer Vault
No piping connected to the plumbing system shall be installed in any transformer vault. Exceptions: A floor drain which discharges ...
Philadelphia Plumbing Code > 9 Soil and Waste Piping > P-901 General Requirements > P-901.1 Discharge > P-901.1.1 Transformer Vault
502.9.5.1 Exhaust Systems, Vaults
Vaults that contain tanks of Class I liquids shall be provided with continuous ventilation at a rate of not less than 1 cfm/ft 2 of floor area ...
2018 Philadelphia Mechanical Code > 5 Exhaust Systems > 502 Required Systems > 502.9 Hazardous Materials—Requirements for Specific Materials > 502.9.5 Flammable and Combustible Liquids > 502.9.5.1 Vaults
5303.16 Compressed Gases, Vaults
vaults complying with Sections 5303.16.1 through 5303.16.14 ...
5704.2.8 Flammable and Combustible Liquids, Vaults
Vaults shall be allowed to be either above or below grade and shall comply with Sections 5704.2.8.1 through 5704.2.8.18 ...
2018 Philadelphia Fire Code > 57 Flammable and Combustible Liquids > 5704 Storage > 5704.2 Tank Storage > 5704.2.8 Vaults
C405.6 [CE] Commercial Energy Efficiency, Electrical Transformers (Mandatory)
Low-voltage dry-type distribution electric transformers shall meet the minimum efficiency requirements of Table C405.6 as tested and rated ...
2018 Philadelphia Energy Conservation Code > 4 [CE] Commercial Energy Efficiency > C405 Electrical Power and Lighting Systems > C405.6 Electrical Transformers (Mandatory)