// CODE SNIPPET
93-511 Tower Lot Coverage
Related Code Sections
184.108.40.206 Administration, Noncombustible Fill for Cooling Towers
Where an existing exterior cooling tower with combustible fill within 15 feet (4572 mm) of the lot line is replaced, such replacement shall ...
NYC Mechanical Code 2014 > 1 Administration > 102 Applicability > 102.4 Additions, Alterations or Repairs > 102.4.2 Special Provisions for Prior Code Buildings > 220.127.116.11 Noncombustible Fill for Cooling Towers
908.3.2 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment, Outside
cooling tower is located not less than 15 feet (4572 mm) from the lot line. The cooling tower is located not less than 10 feet (3048 mm) from any ...
NYC Mechanical Code 2008 > 9 Specific Appliances, Fireplaces and Solid Fuel-Burning Equipment > 908 Cooling Towers, Evaporative Condensers and Fluid Coolers > 908.3 Location > 908.3.2 Outside
Article *317 Maintenance of Buildings, Cooling Towers
All owners of cooling towers shall comply with this article and the rules of the department ...
1022.7 Means of Egress, Fire Towers
Fire towers may be used as exits in lieu of interior stairs provided they comply with all of the requirements for stairways as per Section 1009 ...
NYC Building Code 2008 > 10 Means of Egress > 1022 Exterior Exit Ramps and Stairways > 1022.7 Fire Towers