// CODE SNIPPET
3306.3 Through 3306.9
JUMP TO FULL CODE CHAPTER
Related Code Sections
3306.3 Work Site Safety and Operations, Through 3306.9
2019 Chicago Building Code > 33 Work Site Safety and Operations > 3306 Protection of Pedestrians > 3306.3 Through 3306.9
(5) Wiring Methods and Materials, Through Conductors
Where the pull or junction boxes are used for conductors that do not terminate on the power distribution block(s), the through conductors shall ...
National Electrical Code 2017 of Chicago > 3 Wiring Methods and Materials > 314 Outlet, Device, Pull, and Junction Boxes; Conduit Bodies; Fittings; And Handhole Enclosures > 314.28 Pull and Junction Boxes and Conduit Bodies > (E) Power Distribution Blocks > (5) Through Conductors
(B) Equipment for General Use, Through-Wiring
Luminaires identified for through-wiring, as permitted by 410.21, shall be permitted to be used as a raceway ...
National Electrical Code 2017 of Chicago > 4 Equipment for General Use > 410 Luminaires, Lampholders, and Lamps > 410.64 Luminaires as Raceways > (B) Through-Wiring
714.4.1 Fire and Smoke Protection Features, Through Penetrations
Through penetrations of fire-resistance-rated walls shall comply with Section 7126.96.36.199 or 7188.8.131.52. Exception: Where the penetrating items ...
2019 Chicago Building Code > 7 Fire and Smoke Protection Features > 714 Penetrations > 714.4 Fire-Resistance-Rated Walls > 714.4.1 Through Penetrations
717.6.1 Fire and Smoke Protection Features, Through Penetrations
In occupancies other than Groups I-2 and I-3, a duct constructed of materials in accordance with the Chicago Mechanical Code that penetrates a fire ...
2019 Chicago Building Code > 7 Fire and Smoke Protection Features > 717 Ducts and Air Transfer Openings > 717.6 Horizontal Assemblies > 717.6.1 Through Penetrations