// CODE SNIPPET
801.22 Thermal Safety (Spill) Switches
JUMP TO FULL CODE CHAPTER
Thermal safety (spill) switches shall be installed on barometric dampers, draft hoods, draft diverters, and all other appurtenances that allow dilution air into chimneys or gas vents. Thermal safety (spill) switches shall be interlocked with all of the appliances connected to the same chimney or gas vent.