(2) Thermal Protector
|Motor full-load current 9 amperes or less||170%|
|Motor full-load current from 9.1 to, and including, 20 amperes||156%|
|Motor full-load current greater than 20 amperes||140%|
If the motor current-interrupting device is separate from the motor and its control circuit is operated by a protective device integral with the motor, it shall be arranged so that the opening of the control circuit will result in interruption of current to the motor.