// CODE SNIPPET
7126.96.36.199 Testing Under Positive Pressure
JUMP TO FULL CODE CHAPTER
NFPA 257 or UL 9 shall evaluate fire-protection-rated glazing under positive pressure. Within the first 10 minutes of a test, the pressure in the furnace shall be adjusted so not less than two-thirds of the test specimen is above the neutral pressure plane, and the neutral pressure plane shall be maintained at that height for the balance of the test.