// CODE SNIPPET
417.0 Testing and Balancing Airborne Infection Isolation Rooms and Protective Environment Rooms
JUMP TO FULL CODE CHAPTER
[OSHPD 1, 2, 3, 4 & 5] Prior to acceptance of the rooms, all mechanical systems shall be tested, balanced, and operated to demonstrate to the owner or designated representative that the installation and performance of the systems conform to design intent. All testing and balancing shall be performed by a qualified independent agency certified by the Associated Air Balance Council (AABC): the National Environmental Balancing Bureau (NEBB); or the Testing, Adjusting and Balancing Bureau (TABB).