Note: For energy-related systems under the scope (Section 100) of the California Energy Code, including heating, ventilation, air conditioning (HVAC) systems and controls, indoor lighting system and controls, as well as water heating systems and controls, refer to California Energy Code Section 120.8 for commissioning requirements and Sections 120.5, 120.6, 130.4, and 140.9(b)3 for additional testing requirements of specific systems.
Develop a written plan of procedures for testing and adjusting systems. Systems to be included for testing and adjusting shall include, as applicable to the project:
- Renewable energy systems.
- Landscape irrigation systems.
- Water reuse systems.
Perform testing and adjusting procedures in accordance with manufacturer’s specifications and applicable standards on each system.
In addition to testing and adjusting, before a new space-conditioning system serving a building or space is operated for normal use, balance the system in accordance with the procedures defined by the Testing Adjusting and Balancing Bureau National Standards; the National Environmental Balancing Bureau Procedural Standards; Associated Air Balance Council National Standards or as approved by the enforcing agency.
After completion of testing, adjusting and balancing, provide a final report of testing signed by the individual responsible for performing these services.
Provide the building owner or representative with detailed operating and maintenance instructions and copies of guaranties/warranties for each system. O & M instructions shall be consistent with OSHA requirements in CCR, Title 8, Section 5142, and other related regulations.
Include a copy of all inspection verifications and reports required by the enforcing agency.
|Adopt entire CA chapter||X|
|Adopt entire chapter as amended (amended sections listed below)|
|Adopt only those sections that are listed below||X|
|5.504.4.4 and subsections||X|
|5.507.4 and subsections||X|
|5.508.1 and subsections||X|