// CODE SNIPPET
519.5 Termination of Type II Hood Exhaust System
JUMP TO FULL CODE CHAPTER
The exhaust system shall terminate as follows:
- Rooftop terminations shall terminate not less than 10 feet (3048 mm) from a property line, and the exhaust flow shall be directed away from the roof surface of the roof, not less than 40 inches (1016 mm).
- Horizontal terminations shall terminate not less than 10 feet (3048 mm) from adjacent buildings, property lines, operable openings, and from grade level.
- The termination outlet shall not be directed onto a public way.