// CODE SNIPPET
Section 2404 Temporary and Permanent Tents, Canopies and Membrane Structures
Go To Full Code Chapter
2404.2 Flame Propagation Performance Treatment
Before a permit, when required by Section 109, or approval is granted, the owner or agent shall file with the code enforcement official a certificate executed by an approved testing laboratory certifying that the tents; canopies and membrane structures and their appurtenances; sidewalls, drops and tarpaulins; floor coverings, bunting and combustible decorative materials and effects, including sawdust when used on floors or passageways, shall be composed of material meeting the flame propagation performance criteria of NFPA 701 or shall be treated with a flame retardant in an approved manner and meet the flame propagation performance criteria of NFPA 701, and that such flame propagation performance criteria are effective for the period specified by the permit or approval.
An affidavit or affirmation shall be submitted to the code enforcement official and a copy retained on the premises on which the tent or air-supported structure is located. The affidavit shall attest to the following information relative to the flame propagation performance criteria of the fabric:
- Names and address of the owners of the tent, canopy or air-supported structure.
- Date the fabric was last treated with flame-retardant solution.
- Trade name or kind of chemical used in treatment.
- Name of person or firm treating the material.
- Name of testing agency and test standard by which the fabric was tested.
2404.5 Combustible Materials
Hay, straw, shavings or similar combustible materials shall not be located within any tent, canopy or membrane structure containing an assembly occupancy, except the materials necessary for the daily feeding and care of animals. Sawdust and shavings utilized for a public performance or exhibit shall not be prohibited provided the sawdust and shavings are kept damp. Combustible materials shall not be permitted under stands or seats at any time. The areas within and adjacent to the tent or air-supported structure shall be maintained clear of all combustible materials or vegetation that could create a fire hazard within 20 feet (6096 mm) of the structure. Combustible trash shall be removed at least once a day from the structure during the period the structure is occupied by the public.
2404.7 Open or Exposed Flame
Open flame or other devices emitting flame, fire or heat or any flammable or combustible liquids, gas, charcoal or other cooking device or any other unapproved devices shall not be permitted inside or located within 20 feet (6096 mm) of the tent, canopy or membrane structures while open to the public unless approved by the code enforcement official.
2404.9 Spot Lighting
Spot or effect lighting shall only be by electricity, and all combustible construction located within 6 feet (1829 mm) of such equipment shall be protected with approved noncombustible insulation not less than 9.25 inches (235 mm) thick.
2404.10 Safety Film
2404.12 Portable Fire Extinguishers
2404.13 Fire Protection Equipment
2404.14 Occupant Load Factors
2404.15 Heating and Cooking Equipment
Gas, liquid and solid fuel-burning equipment designed to be vented shall be vented to the outside air as specified in the Fuel Gas Code of New York State and the Mechanical Code of New York State. Such vents shall be equipped with approved spark arresters when required. Where vents or flues are used, all portions of the tent, canopy or membrane structure shall be not less than 12 inches (305 mm) from the flue or vent.
2404.15.5 Cooking Tents
2404.15.6 Outdoor Cooking
2404.15.7 Electrical Heating and Cooking Equipment
2404.16.2 Location of Containers
2404.16.2.1 Containers 500 Gallons or Less
2404.16.2.2 Containers More Than 500 Gallons
2404.16.3 Protection and Security
Portable LP-gas containers, piping, valves and fittings which are located outside and are being used to fuel equipment inside a tent, canopy or membrane structure shall be adequately protected to prevent tampering, damage by vehicles or other hazards and shall be located in an approved location. Portable LP-gas containers shall be securely fastened in place to prevent unauthorized movement.
2404.17 Flammable and Combustible Liquids
2404.17.2 Flammable and Combustible Liquid Storage
2404.18 Display of Motor Vehicles
Batteries shall be disconnected in an appropriate manner.
2404.18.2 Fuel Systems
2404.18.2.1 Quantity Limit
2404.18.4 Places of Assembly
When a compressed natural gas (CNG) or liquefied petroleum gas (LP-gas) powered vehicle is parked inside a place of assembly, all the following conditions shall be met:
- The quarter-turn shutoff valve or other shutoff valve on the outlet of the CNG or LP-gas container shall be closed and the engine shall be operated until it stops. Valves shall remain closed while the vehicle is indoors.
- The hot lead of the battery shall be disconnected.
- Dual-fuel vehicles equipped to operate on gasoline and CNG or LP-gas shall comply with this section and Sections 2404.18.1 through 2404.18.5.3 for gasoline-powered vehicles.
2404.18.5 Competitions and Demonstrations
2404.18.5.1 Fuel Storage
Fuel spills shall be cleaned up immediately.
2404.19 Separation of Generators
2404.20 Standby Personnel
When, in the opinion of the code enforcement official, it is essential for public safety in a tent, canopy or membrane structure used as a place of assembly or any other use where people congregate, because of the number of persons, or the nature of the performance, exhibition, display, contest or activity, the owner, agent or lessee shall employ one or more qualified persons, as required and approved, to remain on duty during the times such places are open to the public, or when such activity is being conducted.
Before each performance or the start of such activity, standby personnel shall keep diligent watch for fires during the time such place is open to the public or such activity is being conducted and take prompt measures for extinguishment of fires that occur and assist in the evacuation of the public from the structure.
There shall be trained crowd managers or crowd manager supervisors at a ratio of one crowd manager/supervisor for every 250 occupants, as approved.
2404.21 Vegetation Removal
Related Code Sections
Section 2404 Tents, Canopies and Other Membrane Structures, Temporary and Permanent Tents, Canopies and Membrane Structures
All tents, canopies and membrane structures, both temporary and permanent, shall be in accordance with this section. Permanent tents, canopies ...
2404.13 Tents, Canopies and Other Membrane Structures, Fire Protection Equipment
Fire hose lines, water supplies and other auxiliary fire equipment shall be maintained at the site in such numbers and sizes as required by the code ...
2404.14 Tents, Canopies and Other Membrane Structures, Occupant Load Factors
The occupant load allowed in an assembly structure, or portion thereof, shall be determined in accordance with Chapter 10 ...
2404.15 Tents, Canopies and Other Membrane Structures, Heating and Cooking Equipment
be separated from other tents, canopies or membrane structures by a minimum of 20 feet (6096 mm ...
2404.16 Tents, Canopies and Other Membrane Structures, LP-Gas
be pointed away from the tent, canopy or membrane structure ...