// CODE SNIPPET
[F] 913.3 Temperature of Pump Room
JUMP TO FULL CODE CHAPTER
Suitable means shall be provided for maintaining the temperature of a pump room or pump house, where required, above 40°F (5°C).
Temperature of the pump room, pump house or area where engines are installed shall never be less than the minimum recommended by the engine manufacturer. The engine manufacturer's recommendations for oil heaters shall be followed.