// CODE SNIPPET
M2201.2.1 Tanks Within Buildings
JUMP TO FULL CODE CHAPTER
Supply tanks for use inside of buildings shall be of such size and shape to permit installation and removal from dwellings as whole units. Supply tanks larger than 10 gallons (38 L) shall be placed not less than 5 feet (1524 mm) from any fire or flame either within or external to any fuel-burning appliance.