// CODE SNIPPET
2703.2.6.1 Tanks Out of Service for 30 Days
JUMP TO FULL CODE CHAPTER
Stationary tanks not used for a period of 30 calendar days or more shall be properly safeguarded or removed in an approved manner. Such tanks shall have the fill line, gauge opening and pump connection secured against tampering. Vent lines shall be properly maintained. Stationary tanks containing flammable and combustible liquid out of service for a period of 30 calendar days or more shall additionally comply with the requirements of FC3404.2.13.