// CODE SNIPPET
P-906.2 Tank Size
JUMP TO FULL CODE CHAPTER
If a condensate or blowoff tank is used, the tank shall be sized to a capacity of 1/3 the total water capacity of the vessel or vessels discharging into the tank.
The tank shall be vented through the roof with galvanized wrought iron, galvanized yoloy, or copper vent pipe not less than two inches in size.