// CODE SNIPPET
G307.3 Tank Inlets and Vents
JUMP TO FULL CODE CHAPTER
In areas of special flood hazard, tank inlets, fill openings, outlets and vents shall be:
- Installed at or above the design flood elevation specified in ASCE 24, Table 7-1, or fitted with covers designed to prevent the inflow of floodwater and outflow of the contents of the tanks during conditions of flooding to the design flood elevation, in accordance with ASCE 24; and
- Anchored to prevent lateral movement resulting from hydrodynamic and hydrostatic loads, including the effects of buoyancy, during conditions of flooding to the design flood elevation, in accordance with ASCE 24.