// CODE SNIPPET
2205.1 Tank Filling Operations for Class I, II or IIIA Liquids
Go To Full Code Chapter
2205.1.1 Delivery Vehicle Location
2205.1.2 Tank Capacity Calculation
2205.1.3 Tank Fill Connections
Delivery of flammable liquids to tanks more than 1,000 gallons (3785 L) in capacity shall be made by means of approved liquid- and vapor-tight connections between the delivery hose and tank fill pipe. Where tanks are equipped with any type of vapor recovery system, all connections required to be made for the safe and proper functioning of the particular vapor recovery process shall be made. Such connections shall be made liquid and vapor tight and remain connected throughout the unloading process. Vapors shall not be discharged at grade level during delivery.
Related Code Sections
2205.1 Motor Fuel-Dispensing Facilities and Repair Garages, Tank Filling Operations for Class I, II or IIIA Liquids
Delivery operations to tanks for Class I, II or IIIA liquids shall comply with Sections 2205.1.1 through 2205.1.3 and the applicable requirements ...
Section 2210 Motor Fuel-Dispensing Facilities and Repair Garages, Marine Motor Fuel-Dispensing Facilities
of Class I, II or IIIA liquids at marine motor fuel-dispensing facilities shall be in accordance with this chapter and Chapter 34 ...
2204.4 Motor Fuel-Dispensing Facilities and Repair Garages, Dispensing Into Portable Containers
Class I, II and IIIA liquids shall not be dispensed ...
3404.2.9 Flammable and Combustible Liquids, Above-Ground Tanks
). Above-ground tanks operating at pressures not exceeding 2.5 psig (17.2 kPa) for storage of Class I, II or IIIA liquids ...
3405.2 Flammable and Combustible Liquids, Liquid Transfer
Liquid transfer equipment and methods for transfer of Class I, II and IIIA liquids shall be approved and be in accordance with Sections 3405.2.1 ...