// CODE SNIPPET
(i) 907.2.1.1 System Initiation of Group A Occupancies With an Occupant Load of 1,000 or More
JUMP TO FULL CODE CHAPTER
Activation of the fire alarm in Group A occupancies with an occupant load of 1,000 or more shall initiate a signal using an emergency voice/alarm communications system in accordance with paragraph (G)(6)(b)(ii)(907.6.2.2) of this rule.
Exception: Where approved, the prerecorded announcement is allowed to be manually deactivated for a period of time, not to exceed 3 minutes, for the sole purpose of allowing a live voice announcement from an approved, constantly attended location.