// CODE SNIPPET
G2422.2 (411.3) Suspended Low-Intensity Infrared Tube Heaters
JUMP TO FULL CODE CHAPTER
Suspended low-intensity infrared tube heaters shall be connected to the building piping system with a connector listed for the application complying with ANSI Z21.24/CGA 6.10. The connector shall be installed as specified by the tube heater manufacturer's instructions.