// CODE SNIPPET
29.10.9 Supervising Stations
JUMP TO FULL CODE CHAPTER
Where off-premises supervision is provided, the system shall transmit at least a general alarm signal.
Alarm signals shall be permitted to be verified prior to reporting them to the fire service, provided that the verification process does not delay the reporting by more than 90 seconds.
Household fire alarm systems shall be programmed by the manufacturer to generate at least a monthly test of the communication or transmission means.
The activation of a keypad fire alarm signal shall require a manual operation of two simultaneous or sequential operations.
Related Code Sections
10.6.11.3.2 Fundamentals, Supervising Station
Automatic-starting, engine-driven generators used to provide secondary power for a supervising station shall comply with NFPA 110 Chapter 4 ...
National Fire Alarm and Signaling Code 2019 of Maine > 10 Fundamentals > 10.6 Power Supplies > 10.6.11 Engine-Driven Generators > 10.6.11.3 Secondary Power Supplies > 10.6.11.3.2 Supervising Station
18.104.22.168.2 Supervising Station Alarm Systems, Supervising Station
Secondary power capacity for all equipment necessary for reception of alarm, supervisory, trouble, and other signals located at the supervising ...
National Fire Alarm and Signaling Code 2019 of Maine > 26 Supervising Station Alarm Systems > 26.6 Communications Methods for Supervising Station Alarm Systems > 26.6.3* Performance-Based Technologies > 22.214.171.124 Secondary Power > 126.96.36.199.2 Supervising Station
29.10.9 Single- And Multiple-Station Alarms and Household Signaling Systems, Supervising Stations
Household alarm systems shall be permitted to be supervised by a supervising station or by a public emergency alarm reporting system ...
National Fire Alarm and Signaling Code 2019 of Maine > 29 Single- And Multiple-Station Alarms and Household Signaling Systems > 29.10 Equipment Performance > 29.10.9 Supervising Stations
3.3.290 Definitions, Supervising Station
) A supervising station that is listed for central ...
National Fire Alarm and Signaling Code 2019 of Maine > 3 Definitions > 3.3 General Definitions > 3.3.290 Supervising Station
14.6.3 Inspection, Testing, and Maintenance, Supervising Station Records
For supervising station alarm systems, records pertaining to signals received at the supervising station that result from maintenance, inspection ...
National Fire Alarm and Signaling Code 2019 of Maine > 14 Inspection, Testing, and Maintenance > 14.6 Records > 14.6.3 Supervising Station Records