// CODE SNIPPET
711.0 Suds Relief
JUMP TO FULL CODE CHAPTER
Drainage connections shall not be made into a drainage piping system within 8 feet (2438 mm) of a vertical to horizontal change of direction of a stack containing suds-producing fixtures. Bathtubs, laundries, washing machine standpipes, kitchen sinks, and dishwashers shall be considered suds-producing fixtures. Where parallel vent stacks are required, they shall connect to the drainage stack at a point 8 feet (2438 mm) above the lowest point of the drainage stack.
Related Code Sections
711.0 Sanitary Drainage, Suds Relief
of a stack containing suds-producing fixtures. Bathtubs, laundries, washing machine standpipes, kitchen sinks, and dishwashers shall be considered suds ...
1009.4 Traps and Interceptors, Relief Vent
Interceptors (clarifiers) shall be so designed that they will not become air-bound where closed covers are used. Each interceptor (clarifier) shall ...
2018 Uniform Plumbing Code of Nevada > 10 Traps and Interceptors > 1009.0 Interceptors (Clarifiers) and Separators > 1009.4 Relief Vent
1112.11.3 Refrigeration, Internal Relief
Pressure-relief valves designed to discharge from a higher-pressure vessel into a lower pressure vessel internal to the system shall comply ...
2018 Uniform Mechanical Code of Nevada > 11 Refrigeration > 1112.0 Pressure-Relief Devices > 1112.11 Discharge From Pressure-Relief Devices > 1112.11.3 Internal Relief
26.3.1* Marine Systems, Relief Valves
Relief valves shall be provided on all wet pipe systems ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 26 Marine Systems > 26.3 System Requirements > 26.3.1* Relief Valves
184.108.40.206 Marine Systems, Relief Valves
Relief valves shall be installed on the tank to avoid overpressurization and false actuation of any dry pipe valve ...
Standard for the Installation of Sprinkler Systems 2016 of Nevada > 26 Marine Systems > 26.7 Water Supplies > 26.7.2 Pressure Tank > 220.127.116.11 Relief Valves