// CODE SNIPPET
Section G2405 (302) Structural Safety
Go To Full Code Chapter
G2405.1 (302.1) Structural Safety
The building shall not be weakened by the installation of any gas piping. In the process of installing or repairing any gas piping, the finished floors, walls, ceilings, tile work or any other part of the building or premises that is required to be changed or replaced shall be left in a safe structural condition in accordance with the requirements of this code.
G2405.2 (302.4) Alterations to Trusses
Truss members and components shall not be cut, drilled, notched, spliced or otherwise altered in any way without the written concurrence and approval of a registered design professional. Alterations resulting in the addition of loads to any member, such as HVAC equipment and water heaters, shall not be permitted without verification that the truss is capable of supporting such additional loading.
G2405.3 (302.3.1) Engineered Wood Products
Cuts, notches and holes bored in trusses, structural composite lumber, structural glued-laminated members and I-joists are prohibited except where permitted by the manufacturer's recommendations or where the effects of such alterations are specifically considered in the design of the member by a registered design professional.
Related Code Sections
Section G2405 Fuel Gas, (302) Structural Safety
structural condition in accordance with the requirements of this code ...
Section 302 General Regulations, (IFGC) Structural Safety
structural condition in accordance with the requirements of the International Building Code ...
Section 302 Occupancy Classification and Use, Occupancy Classification and Use Designation
Occupancy classification is the formal designation of the primary purpose of the building, structure or portion thereof. Structures shall ...