// CODE SNIPPET
126.96.36.199 Storage Within Special Buildings or Rooms
JUMP TO FULL CODE CHAPTER
The maximum quantity of LP-Gas stored in special buildings or rooms shall be 10,000 lb (4540 kg). [58:188.8.131.52]
The construction of all special buildings and rooms specified in 184.108.40.206.2 shall comply with Chapter 10 of NFPA 58 and the following:
- Vents to the outside only shall be provided at both the top and bottom of the building and shall be located at least 5 ft (1.5 m) from any building opening.
- The entire area shall be classified for purposes of ignition source control in accordance with Section 6.23 of NFPA 58. [58:220.127.116.11]