// CODE SNIPPET
6109.11 Storage Within Rooms Used for Gas Manufacturing
JUMP TO FULL CODE CHAPTER
The maximum quantity of LP-gas shall be 10,000 pounds (4540 kg).
- Adequate vents shall be provided to the outside at both top and bottom, located not less than 5 feet (1524 mm) from building openings.
- The entire area shall be classified for the purposes of ignition source control in accordance with Section 6.25 of NFPA 58.