// CODE SNIPPET
2904.5 Storage of More Than 1,000 Cubic Feet to 2,500 Cubic Feet
JUMP TO FULL CODE CHAPTER
Loose combustible fibers in quantities exceeding 1,000 cubic feet (28 m3) but not exceeding 2,500 cubic feet (70 m3) shall be stored in rooms enclosed with 2-hour fire-resistance-rated fire barriers, with openings protected by an approved opening protective assembly having a fire protection rating of 11/2-hours, and constructed in accordance with the construction codes, including the Building Code. The storage room shall be protected throughout by a sprinkler system.