// CODE SNIPPET
34.4 Storage Arrangement
JUMP TO FULL CODE CHAPTER
Any commodities that are hazardous in combination with each other shall be stored so they cannot come into contact with each other.
Safe floor loads shall not be exceeded.
The clearance between stored materials and unit heaters, radiant space heaters, duct furnaces, and flues shall not be less than 3 ft (0.9 m) in all directions or shall be in accordance with the clearances shown on the approval agency label.
Clearance shall be maintained to lights or light fixtures to prevent ignition.
Clearance shall be maintained around the path of fire door travel to ensure the door's proper operation and inspection.
Operation and inspection clearance shall be maintained around fire-extinguishing and fire protection equipment.
Aisles shall be maintained to retard the transfer of fire from one pile to another and to allow convenient access for fire fighting, salvage, and removal of storage.