// CODE SNIPPET
1126.96.36.199 Steel Risers
Related Code Sections
1188.8.131.52 Fuel Gas Piping, Steel Risers
Steel risers, other than anodeless risers, connected to plastic piping shall be cathodically protected by means of a welded anode. [NFPA 54:184.108.40.206] ...
2021 Oregon Plumbing Specialty Code > 12 Fuel Gas Piping > 1210.0 Gas Piping Installation > 1210.1 Piping Underground > 1210.1.3 Protection Against Corrosion > 1220.127.116.11 Steel Risers
G2415.11.4 Fuel Gas, (404.11.4) Protection of Risers
Steel risers connected to plastic piping shall be cathodically protected by means of a welded anode, except where such risers are anodeless risers ...
2021 Oregon Residential Specialty Code (ORSC) > 24 Fuel Gas > G2415 (404) Piping System Installation > G2415.11 (404.11) Protection Against Corrosion > G2415.11.4 (404.11.4) Protection of Risers
8.16.5 Installation Requirements, Protection of Risers Subject to Mechanical Damage
Sprinkler risers subject to mechanical damage shall be protected by steel posts, concrete barriers, or other approved means ...
Standard for the Installation of Sprinkler Systems 2016 of Portland > 8 Installation Requirements > 8.16 Piping Installation > 8.16.5 Protection of Risers Subject to Mechanical Damage
(A) Wiring Methods and Materials, Spacing Intervals — Maximum
be supported at the top of the riser with a cable support that clamps the steel wire armor. A safety device shall be permitted at the lower end of the riser ...
2021 Oregon Electrical Specialty Code (OESC) > 3 Wiring Methods and Materials > 300 General Requirements for Wiring Methods and Materials > 300.19 Supporting Conductors in Vertical Raceways > (A) Spacing Intervals — Maximum
18.104.22.168.6* Hanging, Bracing, and Restraint of System Piping,
When riser nipples are provided in systems requiring seismic protection, they shall satisfy the following equation, unless one of the following ...
Standard for the Installation of Sprinkler Systems 2016 of Portland > 9 Hanging, Bracing, and Restraint of System Piping > 9.3 Protection of Piping Against Damage Where Subject to Earthquakes > 9.3.5* Sway Bracing > 22.214.171.124* Horizontal Seismic Loads > 126.96.36.199.6*